The introduction of radiator thermostatic valves
bulb, is actually a package, simple, filled with liquid, gas, different manufacturers YangZhuang some of the things is different also, we have no matter, anyway, the principle of clear line, the principle is the heat bilges cold shrink, high temperature, the inside of the bulb east began to swell, swelling up to down, the stem pressing down on them, and then turn off the water, hot water into the heat sink and cooling, and then the temperature, temperature package a contraction, the valve stem and play, hot water to continue into the heat sink,spring, his work is a push the valve stem, as long as the bag is not holding up warm, he will push up the stem, and betting bulb, there is a role, everyone see thermostatic valve head is not a number? 12345, corresponding to the temperature, how many degrees, you can twist to several corresponding screw valve head is actually twist spring! Have a spring, elastic changed, betting that spring and bulb of effort, is must expand some more to bulb, so that the corresponding temperature is high, is how many degrees thermostatic valve must be in the outside to close the valve. In addition, in addition to a thermostatic valve 12345 there is a snow gear, don't know everyone noticed no, this is the antifreeze, our heating system is not afraid of water freeze pipe, heat sink? Boiler, air can host has a frost protection, how many degrees below the open pump automatically, automatic ignition, but water have to into the heat sink, thermostatic valve work again at this moment, you have to freeze protection block, he below a certain temperature automatically open, this with host anti-freezing function, anti-freezing effect of leverage. Just as an aside, thermostatic valve has a small problem, is now the general manufacturer is generally high temperature 28 degrees thermostatic valve head, that is to say as long as you at 28 degrees thermostatic valve will automatically close, but the thermostatic valve is mounted on the radiator, radiator temperature 28 degrees, on the edge of the room temperature may also only 20 degrees, some clients will say 20 degree is low, I'm cold ~ ~ ~ ~ so when you install thermostatic valve and customers say ahead of time, as long as the thermostatic valve, room temperature is not high, not wear a separates the effect of running in the room
To that end, Zhuhai Edison Smart Home Co., Ltd. has successfully built a solid foundation and infrastructure for wireless thermostat manufacturing.
See reviews of the latest trend in thermostats industry at Edison HVAC Valves, and see the best that work in just minutes! Visit us right away!
hvac expansion valve motorized valve are used largely for ac compressor control valve such as hvac expansion valve.